Views: 3 Author: Site Editor Publish Time: 2023-09-12 Origin: Site
Installation Conditions for the Ultra-pure Water System
Feed Water: Well water.
Operating Mode: Automatic control.
Design Layout: From feed water tank to 2nd stage reverse osmosis system to pure water tank to EDI ultra-pure water system.
Power Supply: 380V.
Installation in a plant with an area of 15 square meters and an operating room equipped with underground drainage system.
Application: Production of new materials.
Water Production Capacity: ≥2m3/h.
Water Quality: Outlet resistivity ≥15 megaohms. The equipment should incorporate Dow reverse osmosis membranes and fully automatic control valves.
Process Utilized by the Equipment
Feed water tank + quartz sand + activated carbon + anti-scalant filter + primary high-pressure pump + primary reverse osmosis automatic control device + secondary high-pressure pump + secondary reverse osmosis system + pure water tank + EDI ultra-pure water equipment + ultra-pure water tank + pipeline pressure pump + mixing tank.