Views: 0 Author: Site Editor Publish Time: 2023-09-12 Origin: Site
0.5T Two Stage Reverse Osmosis Water Treatment System Installation Conditions
Raw water source: Tap water.
Operation mode: Automatic control.
Design boundary: From the outlet of the raw water tank to the outlet of the pure water tank.
Power supply: 380V.
Installation facility: Equipment installation operation room of 20 square meters with underground drainage system.
Water usage: For catering purposes.
Water production capacity: ≥0.5m3/h, 1800 bottles/hour, 200 barrels/hour.
Water quality: Conductivity of the produced water ≤5μs/cm.
Complies with GB5749-2006 Drinking Water Hygiene Standard, J94-1999 Drinking Purified Water Standard, GB 17324-2003 Bottled (Barrel) Drinking Purified Water Hygiene Standard.
Process adopted by the equipment
All-in-one machine: Raw water tank + Quartz sand + Activated carbon + Resin + First-stage high-pressure pump + First-stage reverse osmosis + Second-stage high-pressure pump + Second-stage reverse osmosis + Pure water tank + Terminal water supply system.
We supply a wide range of products which include 500 lph water purifier ro system, 2000 lph ro system, 1000 lph ro system and 250 lph ro system.