Views: 0 Author: Site Editor Publish Time: 2023-09-12 Origin: Site
Reverse Osmosis Equipment Installation Conditions
Source Water: Tap water.
Operation Mode: Automatic control operation.
Design Boundary: From the outlet of the raw water tank to the outlet of the purified water tank.
Power Supply: 220 volts.
Installation Workshop: 16 square meters equipment installation control room, equipped with underground drainage system.
Water Usage: Bottled drinking water.
Water Production Volume: ≥0.5m3/h.
Water Quality: Outlet conductivity ≤15μs/cm.
Compliance with GB5749-2006 Drinking Water Health Standards, J94-1999 Drinking Water Purification Standards, GB 17324-2003 Bottled Drinking Pure Water Health Standards.
Equipment Utilization Process
Integrated Machine: Raw water tank + Quartz sand + Activated carbon + Resin + First-stage high-pressure pump + First-stage reverse osmosis + Purified water tank + Bottled water filling system.
We supply a wide range of products which include 500 lph water purifier ro system, 2000 lph ro system, 1000 lph ro system and 250 lph ro system.