Views: 1 Author: Site Editor Publish Time: 2023-09-12 Origin: Site
mineral water purifier plant Conditions
Source Water: Tap water.
Operation Mode: Automatic control.
Design Scope: From the outlet of the raw water tank to the outlet of the purified water tank.
Power Supply: 380 volts.
Installation Space: A 50 sqm equipment installation control room with an underground drainage system.
Water Usage: Bottled drinking water.
Water Production Capacity: ≥0.25 m3/h.
Water Quality: Effluent conductivity ≤12μs/cm. The equipment adopts imported reverse osmosis membranes and functional control heads.
Comply with the hygiene standards for drinking water: GB5749-2006, J94-1999, GB 17324-2003 for bottled (barreled) drinking purified water.
mineral water purifier plant Process Process
All-in-One System: Raw water tank + Quartz sand + Activated carbon + Resin + 1st stage high-pressure pump + 1st stage reverse osmosis + Automatic control device + Purified water tank + Bottle caps removing machine + Filling system.
We supply a wide range of products which include 500 lph water purifier ro system, 2000 lph ro system, 1000 lph ro system and 250 lph ro system.